The 2020 National Electrical Code has rolled out a host of changes.
Some, in my opinion, have been long overdue. Just as an example, the 2020 NEC has four brand new articles, Articles 242, 311, 337, and 800. This came after 3700-plus public inputs and 1400 first revisions!
Here we’ll discuss one of the first changes. It appears in Article 110.22 – Identification of Disconnect Means.
Article 110.22(A) states:
“Each disconnecting means shall be legibly marked to indicate its purpose unless located and arranged so the purpose is evident. In other than one- or two-family dwellings, the marking shall include the identification of the circuit source that supplies the disconnecting means. The marking shall be of sufficient durability to withstand the environment involved.”
The wording here is well-phrased and specifically mentions a clear “purpose” of the disconnect means. In other words, one should never have to guess what the disconnect is providing power for. Anything beyond a visible conduit to a local load indicates a clearcut need for proper labeling of the disconnect.
The “identification of the source that supplies the disconnecting means” is a critical addition to the 2020 NEC. For ALL disconnects, the associated power supply must now be clearly indicated on a label that is legible and clear! So much for disconnects that have no labels whatsoever, or those I have seen that simply say “motor” with no motor anywhere within sight.
OSHA Subpart S 1910.303(e) has addressed the requirement for labeling electrical equipment for years.
The OSHA statement, however, is a little vague. It is worded as follows:
1910.303(e)(1) Identification of manufacturer and ratings. Electric equipment may not be used unless the following markings have been placed on the equipment:
1910.303(e)(1)(i) The manufacturer’s name, trademark, or other descriptive marking by which the organization responsible for the product may be identified; and
1910.303(e)(1)(ii) Other markings giving voltage, current, wattage, or other ratings as necessary.
The “other markings….as necessary” statement leaves a wide path for interpretation. Having spoken over the years to several Federal and State OSHA inspectors, I consistently hear a basic tenet: these “other markings” should include the panel voltage, the panel ampere rating, the name of the panel, where it derives its power, and any and all equipment it feeds. This sounds reasonable for any electrical installation. Any electrician, engineer, or technician would certainly appreciate seeing a label with such appropriate information in a readily-available format.
NEC is Law
The 2020 NEC change referenced above certainly brings a legal perspective (enforceable by law once adopted by the state). The requirement to identify the equipment disconnect as to its purpose and its subsequent power supply in a method that will hopefully last the life of the panel itself will remove confusion by making these items crystal clear. I, for one, have seen enough “labels” that faded out in the 1970s and were never corrected, leaving the equipment’s details for a private eye to discover. This is truly unacceptable in our industry.
Other references for labeling electrical equipment appear throughout the 2020 NEC, as the following excerpt from 408 Switchboards, Switchgear, and Panelboards states:
408.4(B) Source of Supply. All switchboards, switchgear, and panelboards supplied by a feeder(s) in other than one- or two-family dwellings shall be permanently marked to indicate each device or equipment where the power originates. The label shall be permanently affixed, of sufficient durability to withstand the environment involved, and not handwritten.
In addition to arc flash labels, nominal voltage, and any other necessary markings, the following example shows what one should see when approaching electrical equipment:
Labels similar to this remove any guessing game as to the equipment’s purpose, and provide direction for quick access to panel or equipment supply in the case of a need for urgent disconnection. Let’s all do our part in ensuring electrical equipment is properly identified, and by all means, keep electrical safety at the forefront of our minds.
For further reading:
If you need training on the NEC or on electrical safety, see our training schedule online.